to 1000 A busbarIP40/55
the enclosure is made from galvanised steel sheet formed to provide
a rigid high strength profile.
Conductors are made from either electrolytic copper or aluminium
that is tin plated along its entire length.
The shuttered outlet points are positioned at 500mm. spacing on
alternate sides of the enclosure and are opened by the insertion
of the tap-off box.
made from galvanised steel with painted covers, it is mounted at
the beginning of the line.
The box is provided with an undrilled cable plate in aluminium.
Connection is made by means of stud terminals.
feed box with switch: similar in construction to the end feed box, this
unit has an on-load switch.
this box can be positioned at any joint between busbar sections;
cable connection is the same as the end feed box.
included in the system are horizontal elbows, vertical elbows, tees
and fourway units which allow almost any route to be planned.
Hangers: two types of brackets
permit the busbar trunking to be fixed to walls or ceilings.
A number of brackets are also available to satisfy every other requirement.
The installation of a fixing bracket every 3m. maximum is advised.
this unit will allow a trunking run to be split into two legs and
comes complete with a switch.
box 63¡À125 A/250¡À400 A: the tap-off box meets high safety standards; when
the cover is open, the internal fuses are de-energised by a built-in
off-load insulator which enables the fuses to be changed in complete
box (125¡À1000 A) with fuseswitch: these tap-off boxes are used whenever
the users on-load insulation is required.
covers and accessories: for closing the line, with the proper accessories;
IP40 or IP55 protection is achieved.